To choose the right regulator, it is necessary to verify the pressure and the workflow of burning appliance, the type of the gas (GLP or GN) and the entrance and exit connections of installation (do not forget to verify the quantity of gas is provided).
Single Stage: The pressure is directly reduced to the operating pressure of the burning appliance. 1º/2º Stage: The pressure is reduced to an intermediary value (1ª stage) and then is reduced again to an operation pressure of the burning appliance (2ª stage).
The ONLY function of gas regulator is regulate the PRESSURE according to your installation necessity. (the Regulator do not have the function to block the gas flow)
The piping diameter must be defined according to the gas consumption of installation, the distance among the gas battery and the burning points and the pressure that is on system (please, verify the installation Norm NBR 15.526)
The validity of Aliança´s Regulators are 5 years, according to rule of INMETRO Nº 6 of January 8th, 2013. In case the regulator is violated, changed or used in an improperly way, this validity will not be applicable. .
All gas regulator has a hole on the cover that is the air breather. Through this breather, the rubber diaphragm can work and consequently regulate the exit pressure.
ATTENTION – Through the regulator breather just can exit the air.
Never obstruct the hole of air breather.
The gas regulator for GLP cannot be used in an installation for GN, because the pieces regulation are incompatible with the installation needs. (Work Pressure GN = 220 mmca/ Work Pressure GLP = 280 mmca)
ATTENTION – If you use a GLP gas regulator gas in an GN installation, or vice-versa, the validity of gas regulator will no longer be effective.
504/01 – Domestic Regulator 1,0kg/h GLP, has a bigger body from 1,0kg/h category and can be used until 5,0m of distance from gas cylinder to the stove.
505/01 - Domestic Regulator 1,0kg/h GLP, has a smaller body and can be used until 5,0m of distance from gas cylinder to the stove.
506/01 – Domestic Regulator 2.0kg/h GLP, has a cover fixed with a screw and can be used until 10,m of distance from the gas cylinder to the stove.
ATTENTION - All models (504/01, 505/01 and 506/01 can be used in domestics stoves of 4/5 burners head).